High Pressure Fans and Filters
Two Aspiration Fans in a Maize Cleaning Section
In the wheat and maize milling industry, there are typically three distinct categories of fans used in the milling process. They are namely Low Pressure Fans, operating at 1.5 to 4 kPa, Medium Pressure Fans, operating around 5 to 7 kPa and High Pressure Fans, operating at 9 to 14 kPa. Considering the pressures utilized in other industrial processes, in the pressures used on fans in the milling industry are in actual fact, relatively low.
Low Pressure Aspiration Fans
This group ranges from 5 m³/min typically on small single aspiration points, i.e. bin top filter/fan units, up to about 500 m³/min for a large mill or silo aspiration system. Seldom one finds a system bigger than that in the milling industry. The pressure range is usually between 150 mm WC where the fan is servicing a gravity operating machine and is in series with the general exhaust system and 400 mmWC. On large aspiration systems, with ducting extending from the top floor of the mill right throughout the building and including a filter unit, pressures can be as high as 400 mm WC but seldom higher. The largest motor that one is likely to find on an aspiration fan in the milling industry, would be 45-55 kW.
For example, a low pressure fan delivering 500 m³/min at 400 mmWC pressure, would have a shaft power requirement of 44 kW and the fan manufacturer would install a 55 kW motor.
There is a wide range of impellor designs and sizes and the low pressure fans are identified by wide impellors and diameters up to 1100 mm when the fan is directly driven, utilizing a 4 pole motor. A low pressure fan delivering 300 m³/min, would have an impellor width of approx 300 mm wide, whereas a high pressure fan delivering 300 m³/min, would have approx 80-100mm wide impellor on the circumference. Low pressure fans can also be directly driven with a 2 pole motor which results in considerbly smaller housings, impellors, but a negative is a considerably noisier fan.
Aspiration Fan servicing two Dry Destoners
Medium Pressure Pneumatic Fans
This is a small group of fans used in the milling industry and usually for single line conveying, e.g: hammermill lifts, thermo pneumatic drying or cooling lifts in maize mills, conveying the thru's from new generation degerminators or wheat debranning machines. They are not in any way identifiable from the outside from high pressure fans. For example, an MP fan handling 60 m³/min at 650 mm WC, would have a wheel 50 mm wide and about 700 mm in diameter. A HP fan could be accommodated in the same fan housing with the same 60mm wide wheel but with a diameter of 900mm and delivering 1100 mmWC in the high pressure range.
The medium range of pressure can be applied because the air to stock ratio is high. On drying and cooling lines, the air to stock ratio is sometimes as high as 0.30 kg product to 1 kg air to maximize drying or cooling effect. A typical example of an application to employ a medium pressure fan, would be the conveying of the thru's of a new generation high compression degerminator. The thru's can be between 15 to 20% of the machine throughput i.e. up to 1400 kg/hour on a 200 mm diameter lift with 50 m³/min. In a normal mill layout such a lift would be about 30 meters in length and have a MP fan with 500-700 mmWC absorbing 7.8 kW and driven by an 11 kW motor. The air to stock ratio would be less than 0.4 kg product to 1 kg of air. The air volume is not only conveying the thru's material from the degerminator, but also creating a negative pressure within the machine and improving the machine's performance. The air blown into the machine from the onboard fan to keep the screen clean, is also evacuated by the thru's pneumatic transport. There is no limit to the number of individual lines you can connect to a medium pressure fan, so long as there is sufficient air volume for all the individual lines and the negative pressure is sufficient to overcome all plant resistances.
High Pressure Fan in a Flour Redressing Plant
High Pressure Fans
These fans are applied for the conveying of intermediate stocks in the milling process and the range of fans found in the milling industry, is up to 330 m³/min. A mill pneumatic conveying system can comprise of as many as 30 lines or more on a single fan/filter system, depending on pipe sizes and stock quantities.
To drive a HP fan with 330 m³/min at 1400 mm WC, would require approx. 102 kW shaft power, depending on the efficiency of the impellor. The application of a 110 kW motor, can be border line and difficult to start in such a situation, resulting in the next motor size, 132 kW, being installed. One never sees motors bigger than 132 kW on HP Fans. Another limiting factor on HP fans with 330 m³/min, is that they require extremely large filters to service the air filtration process. Although it is possible to have two smaller filters servicing one HP fan, one has to take care that the air volumes are split proportionately in relation to the filter sizes. The filters do not have to be the same size. A single filter for 330 m³/min usually requires the application of a 104 bag filter with 3 meter bags generating 104 m² of filter area. The range of pressures applied on HP Fans, can be from 800 mm WC in maize or wheat mills with 10 to 15 meter lifts up to 1450 mm WC in lines as long as 35 meters (total vertical and horizontal piping). The impellors used on high pressure fans vary in shape and size and the following are generalizations:
Information required by fan manufacturers from the cereal milling engineer, to supply a new fan, would be:
Fans should always be placed on anti vibration mountings.
Inlets and outlets need rubber damper connections.
Fans should have large inspection doors to carry out periodic cleaning of any build up on the impellor. Cleaning the impellor regularly saves motor bearings and reduces vibrations considerably.
High Pressure Fan Servicing Flour Redressing Plant
2 X 110 kW High Pressure Fans in Large Capacity Maize Mill.
The fan characteristic or performance curve, is the fan manufacturers computer generated document, which is developed considering the customer's volume and pressure requirements. In the illustrated fan curve below, the fan was designed to operate producing a volume air flow of 150 m³/min at the fan inlet at a negative pressure of 1200 mmWC, Point A. One of the biggest problems with mill pneumatics, is that plant operators open the air control valves on the individual lines more than required, resulting in more air volume consumed than is necessary to convey the product quantity on that line. When individual aircotrol valves on the various lines are opened more than required, the operating point on the curve moves to the right- the result is, the air volume flow increases in the example to Point B, where the air volume throughput increases to 160 m³/min, but the pressure drops to 1150 mmWC. Since all pneuamtic systems have a reserve in the design, this may not be a problem, but if the curve moves further to the right with valves being further opened, the air volume increases to 170 m³/min, but the pressure drops further to 1100 mmWC, Point C.
It may well be at Point C on the curve, that quite a number of critical lifts, i.e. the lifts with the highest individual negative pressures, could start choking and a typical reaction of a plant operater to a choking lift, is to further open air control valves on the problematic lines. Any further movements to the right on the curve, beyond Point C, exaggerates the problem further. The ideal fan curve would be one that is as flat as possible, i.e. any movements to the right of the design point, Point A, results in minimal pressure differentials. One does see flatter and steeper fan performance curves from various fan manufacturers.
Units of pressure most commonly used in mill pneumatic and aspiration systems, are as follows:
In the milling industry, to remove dust from the pneumatic conveying air before exhausting to atmosphere, cyclones or filters are used.
In urban areas, the use of cyclones is almost impossible due to air pollution regulations, as cyclones are not 100 % efficient. In the case of smaller air volumes, an accurately sized cyclone can perform well, but lacks the efficiency of a filter.
The formula for cyclone sizing design, is - Volume m³/min ÷ m² (cyclone cross sectional area)
Example: 200 m³/min air volume can be handled on a 1500 mm diameter cyclone.
1500 mm diameter = 1.5 meter diameter = 1.76 m² cross sectional area
200 m³/min ÷ 1.76 m² = 113 m/min
This value of 113 m/min, is referred to as the volume specific loading figure of a cyclone and should be between 90 and 130 m/min
Loading a 1.5 m diameter cyclone with for example 250 m³/min of air, will result in a very high airspeed through the cyclone, which in turn will decrease the separating efficiency of the cyclone and also result in a higher resistance (pressure drop) across the cyclone.
Filters are available in two different forms: Rectangular cross section filter housings and round filter housings.
In the maize and wheat milling industry, by far the most commonly used is the round housing. These filters in turn are equipped with two very different bag rinsing (cleaning) systems.
The use of normal compressed air from the mill's compressed air network - rinsing at 4.0 to 6.0 Bar pressure.
The installation of a low pressure system, operating at 0.5 Bar and the compressed air being produced by a rotary piston blower.
In wheat and maize mill aspiration systems, the specific filter loading factor can be as high as 9 m³/min air/per 1 m² Nett filter surface area when light dust from equipment aspiration has to be filtered.
To calculate the filtration speed on a filter one divides the volume in m³/min by the total nett surface area of the filter cloth, eg. on a pneumatic high pressure fan with 60 m³/min, one would require 18 m² filter cloth.
The resultant figure is a filtration speed which is expressed in meters per minute - m/min, i.e. 60 m³/min divided by 18 m² = 3.33 m/min filtration speed.
On wheat and maize mill pneumatic conveying systems, the filter load factor should not be higher than 4 m³/min per 1 m² Nett filter surface = 4 m/min. The bigger the filters area the better. We design mill pneumatic conveying filtration systems on 3 to 3.5 m/min, which has an initial higher installation cost, but results in lower operating costs from the point of view of energy consumption, less resistance across the filter. Another benefit is that the duration between filter bag changing exercises can be extended. The life of filter bags depends to a large extent on well designed super efficient mill pneumatic receiving cyclones. In well designed mill pneumatic conveying systems, with correct sized receiving cyclones, it is possible to see very little filter flour.
Filter in Flour MIll with Air Inlet below the Filter Bags
Batch of Cyclones in Large Capacity Maize Mill
Example of 2 X Filters Connected to one High Pressure Fan
Filter and Manifold matrix in Large Capacity Wheat MIll
Pneumatic Cyclone Floor in Large Capacity Maize Mill. In the foreground - Large Cyclones for Drying and Cooling lifts
5 X Large Filters in Outlet Cyclones in Large Capacity Maize Mill
2 X Filters Connected to 1 Manifold to ensure a Filter to Air Ratio of 2,6
Manifold from Filters into High Pressure Fan in Medium Capacity Flour Mill
2 X Collecting Manifolds from evenly split Receiving Cyclones going to Filters
Manifold Ducting from 2 Filters into Fan
Aspiration Fans in very high capacity Packing Department
Aspiration Fan in Large Capacity Maize Pre-cleaning Plant
High Pressure Fans in Large Capacity Maize Mill
High Pressure Fans with Automatic Butterfly Valves infront of Fan
Medium Pressure Fan servicing the Thru's from 4 High Compression Degerminators
Blowline Cyclones and Aspiration Ducting in Large Capacity Packing Plant
|Back||Back to top|